House and Grounds Meetings
Current open work order items
Air Condition layout
Fire Lane, Parking Marking
Facility Layout Drawing
Building Original Construction Year 2000
Building Phase 2 Year 2005
Audio Visual prewire in original 2000 building
LED Retrofit program
Thermostat replacement program
Hand Sinks in children’s area
1. House and Grounds Meetings
H & G Minutes, July 2021 house and grounds agenda
H&G Minutes for 71421
H & G Minutes, Oct 20, 2021 (2)
H & G Minutes, Nov. 17, 2021
Do we have notes from the December H & G meeting?
No Jan 2022 H & G meeting
H & G notes Feb 2022
H & G notes Mar 2022
H and G notes Apr 2022
2. Current open work order items
Here are the OPEN WORK ORDERS live sheet
3. Sprinkler layout
Church Sprinkler with heads PDF file 11×17
Hunter ICC sprinkler OM_ICC_DOM Hunter controller on the west wall, Key is in the mower shed, or the outside closet
Orbit Weathermaster rain sensor, bad reviews, it is in bypass mode
4. Air Condition layout
Here is the link to the Google Sheet for Air Conditioners
Cost breakdown by unit This is the 4 pager that gathers cost history on each unit.
Link to current manuals from Lennox
Interface to LonTalk Lennox units this is the board that shows error codes, Installed in 23, 24. These are MI-6 Rev A boards
TDI Seasonal description:
Three HVAC contractors VENDOR:
HVAC Technical Junior Morales 817-428-0124
Proposed Seasonal: BLANK MAINTENANCE
Morales quote: First Baptist.
Lead time on the equipment is 17-18 weeks , Bryant equipment is not available!!
18 weeks quote from May 1 . Current deliveries are not being delivered on time.
Brandon is contact 817 721 8724
Technician Alex 817 304 6009
Requests for 2022, May9 visit:
1. Children’s gym not cooling, Possibly RTU8.
Requests for 2022, May10 visit: PDF file attached.
1. Complete extensive seasonal inspection early.
2. Evaluate the following known issues:
2.1 RTU 2 has been reported not cooling in the past.
2.2 RTU 19 shows code 6.06 L2
2.3 Possibly RTU24 has loud electrical hum when starting
2.4 RTU 13 has wet spot at temporary HP service valve
2.5 RTU 20 has white wire to thermostat disconnected
3. We might buy a spare compressor, P/N ZR46K3-tf5-250.
3.1How many RTU units would that service?
4. We have committed to replacing 3 units in September.
4.1 RTU 1 because the Gas burner is failed
4.2 RTU 4 because the Gas burner is failed
4.3 RTU 2 or RTU8, depending upon your findings
5. 4 RTU on sanctury have failed heat exchangers….
(BCI Mechanical Kyle Minter 940-565-1010 , did not contact them for a quote..)
(Grant Air Conditioning Dale Kinson 817-332-7979)
5. CO2 monitor
2 in the kitchen
6. Fire Lane, Parking Marking
7. Toilet flush
Here is the autoflush units installed on each urinal.
8. Facility Layout Drawing
9. Building Original Construction Year 2000 plans
This was done by Crone Engineering, evidently out of business.
10. Building Phase 2 Year 2005 plans
Here are the electrical plans from the 2005 expansion.
fbcjustinPlan2005_Mechanical These are the large format prints from the architect:
Henry S Quigg, Richmond Group, 12200, Stemmons #317, Dallas, Texas 75234, Office 972.484.5977, Cell 214.244.8555
11. Audio Visual pre-wire in original 2000 building
12. LED Retrofit program
Denton Electric Service, Nathanial knows the GPS timers, wiring. Timothy
South Exterior lights
West exterior lights
4 foot fluorescent in Foyer
On charlas desk, batteries are back order.
14. Thermostat replacement program
Installed SENSI model ST55, Snensi APP for thermostats: u email@example.com p Media2737
15. Hand sinksink children’s area
17. Roof leaks
Kids gym, north wall, above cabinets, west of glass doors. Red stain on rafter.
South wall, east to west rafter, 10 foof section, area of the west window, 2 feet north of wall.
East wall, looks like the curb of the AC unit,
Adults classroom, north of conference room, ceiling tile stained.
17. Lawn Equipment
2 qts 10w-30
Zero: 74492 sn 407200497, engine
Blower Stihl BG86